Vulkem 45 is a one-part moisture curing, pour grade polyurethane joint sealant caulk. Vulkem 45 does not require a primer on most construction materials.
Vulkem 45 has been formulated for sealing expansion and control joints in parking garages, plazas, terraces, highways, bridges, swimming pool decks, reservoirs, sewage treatment plants, floor and sidewalk joints. Gasoline and diesel fuel resistant, extraordinary adhesion, cohesion, abrasion and tear resistance are inherent in the base polymer. Vulkem 45 is suitable for use in continuous water immersion.
• Do not apply over damp or contaminated surfaces.
• Use with adequate ventilation.
Quart (850 ml) cartridges, packaged 12 per case.
Vulkem 45 meets the requirements of U.S. Federal Specification TT-S-230C, Type 1, Class A and ASTM C920, Type S, Grade P, Class 25 Use T, M, A and O. Vulkem 45 passed Canadian Standard 19GP16a. USDA Approved. Tested and Certified to ANSI/NSF Standard 61 Drinking Water System Components health Effects.
Basic Coverage Rules:
1-Quart cartridge will cover 10-12 linear feet of ¼ inch wide by ¼ inch deep - Use backer rod size 3/8 inch diameter
1-Quart cartridge will cover 6-7 linear feet of ½ inch wide by ½ inch deep - Use backer rod size 7/8 inch diameter
1-Quart cartridge will cover 3-5 linear feet of 1 inch wide by ½ inch deep - Use backer rod size 1-1/8 inch diameter
Other Installation Products:
Joint Design: May be used in any horizontal joint design in accordance with accepted architectural/engineering practice. Joint width should be 4 times anticipated movement, but not less than ¼ inch (6.4 mm) wide.
For joint ¼ inch (6.4 mm) to ½ inch (12.7 mm) wide, the width to depth ratio should be equal. Joints ½ inch (12.7 mm) wide or greater should have a sealant depth of ½ inch (12.7 mm). Minimum joint size is ¼ inch by ¼ inch (6.4 mm by 6.4 mm). For joints larger than 1 inch (2.5 cm); call for assistance.
For good adhesion, the joint interface must be sound, clean and dry. Depending on the substrate, or presence of form release agents, masonry waterproofing, dust, loose mortar or laitance, architectural paints or finishes, the joint surface may require a thorough wire brushing, grinding, sandblasting, solvent washing and/or primer.
Tooling & Cleaning:
Tooling is generally not required. Where necessary, light tooling can be done immediately. Excess sealant and smears adjacent to the joint can be removed with Xylol or Toluol before sealant cures.
Joint Backing- Bond Breaking Tape:
Closed cell polyethlyene backer rods are preferred as joint backing to control depth of sealant bead. Where depth of joint will prevent use of joint backing, an adhesive backed polyethylene tape should be installed to prevent three side adhesion. Joint backing must be dry at time of sealant application.
Vulkem 45 is easy to apply with conventional caulking equipment. At 75°F (23.9°C), 50% R.H. a skin forms within 24 hours. Curing continues at the rate of 1/16 inch (0.16 mm) depth per day. The cure rate is reduced at lower temperatures and less humidity
Not intended for use by persons with pre-existing lung disorders or breathing problems or by those who have had a reaction to iscoyanates. Do not breathe vapors. Reports have associated repeated and prolonged occupational exposure to solvents with permanent brain and nervous system damage. Contains less that 115 gm of VOC per liter less water and less exempt solvent. (New Jersey statement: Contents of this container contain less that 1.0 pounds per gallon of VOC less water). Solvent contained is photochemically reactive.
Vapor harmful. May cause skin, eye and lung irritation and allergic respiratory reaction. Potential sensitizers. Long term overexposure to xylene may cause adverse kidney, liver or fetal development effects. Avoid ingestion, inhalation of vapors and contact with skin, eyes and clothing. Use only in well ventilated areas. If vapor concentration is unknown or exceeds exposure limits (e.g. TVs/PELs), wear suitable respiratory protection as indicated on the MSDS. Wear suitable eye, face and hand protection and other protective apparel. For additional health and safety information read the current MSDS carefully before using this product.
Get medical attention immediately for any significant overexposure.
Leave area to breathe fresh air. Avoid further overexposure.
Flush immediately with running water for 15 minutes and get medical attention.
Wash thoroughly with hand cleaner followed by soap and water. Get medical attention immediately if rash or other disorders develop
All prices are in USD.